The AVTECH Light Tower & Relay Adapter
is required to connect the Light Tower, Light Tower audible and visual alarm or the Relay Switch Sensor to AVTECH's Room Alert 32W, 32E, 12E or 3E environment monitors. It also includes one (1) relay switch that can be used to turn on/off low voltage devices via the Room Alert web interface, Room Alert Manager or automatically in response to an alarm condition going in or out of an alert stage. Common uses for this relay include connecting to a building alarm panel or other notification system to automate advanced alerting and response to static building alarms that do not notify staff. Users can also connect it to a generator, back up HVAC unit, fan or water pump to turn it on/off in response to an alert condition. The built-in relay supports loads up to 0.3A at 125VAC or 1A at 24VDC.
This is an instant 'Plug & Play' adapter that connects directly into the 'Light Tower / Relay' Port on the Room Alert 32W, 32E and 12E monitors, or the Room Alert 3E via the included 25´ RJ-11 Cable, and to a Light Tower or Relay Switch Sensor via a connection cable. Connect the relay by using standard speaker wire, twisted pair or any reliable low voltage 2-wire cable. The AVTECH Light Tower & Relay Adapter is ONLY compatible with AVTECH's Room Alert 32S, 12S, 32W, 32E, 12E and 3E at this time, or Relay Switch Sensor. A 5V 1A International Power Adapter is included that provides independent power to the attached devices.
Call one of our experienced Product Specialists for answers or send us an email at Sales@AVTECH.com
Protect Your Facility... Don't Wait Until It's Too Late!
Remember, 'Proactive Monitoring' is always better than 'Disaster Recovery'.